We were called out to an RP that was dumping out of the relief valve. Let’s see why!
After taking it apart, it looked pretty clean. It appeared to be the spring in the check valve was not seated correctly. I may have been from turning the water on too quickly. The relief valve is a little too low. It is supposed to be 12″ above Grade.